RESET MODBUSOmnie 'O' -> Cogs -> General Params -> System Set Up -> Reset Modbus -> POP UP: Yes
You'll see a please wait screen while the Control Hub communicates with the Omnie Wiring Centre, once the Wiring Centre has been reset there will be a flashing red LED (flashing once with a 3 second delay).
LINK WIRING CENTREOmnie 'O' -> Cogs -> General Params -> System Set Up -> Wcentre Settings -> Add Wcentre -> Automatic -> With el.mix -> POP UP: Yes
You'll see a Warning pop up that will instruct you to press the U1 button on the Omnie Wiring Centre. See fig. 1
Fig. 1: Press U1 popup
Once you've pressed U1 on the Omnie Wiring Centre the red LED will stop flashing while it communicates with the Control Hub. After a successful communication the red LED on the Wiring Centre will be flashing 3 short flashes and the pop up box will have disappeared from the Control Hub.
NOTICE: If the Wiring Centre gets stuck on the warning pop up and will not connect please check that all the wires have a solid connection. We recommend taking the wires out of the terminal block, winding the terminal block screws to the downward position and reinserting the wires making sure there is a solid connection. If you do this make sure to perform a Modbus Reset before you attempt to connect the Wiring Centre again.
ADD SENSOROmnie 'O' -> Cogs -> General Params -> System Set Up -> Wcentre Settings -> Add Sensor -> Manual Mode -> SELECT: Wcentre 1 -> PRESS: TICK -> Add 1 into the box -> PRESS: TICK -> Assignment -> SELECT: room number 1 -> SELECT: TICK -> INPUT: Sensor Serial Number -> PRESS: OK
TOP TIP: The sensor LED will stop flashing once connected at this stage
START SYSTEMOmnie 'O' -> Cogs -> General Params -> System Set Up -> System Start -> POP UP: Yes
TOP TIP: The Control Hub will now communicate with the Wiring Centre, the red LED will stop flashing and some green LED's along the A rail will turn on
CHECK TEMPERATUREOmnie 'O' -> House with Magnifying Glass
You should have 1 room showing on the screen reading two temperatures. See fig. 2. If there is a reading on the top right of the room box then the Sensor, Control Hub and Wiring Centre are working as expected.
TOP TIP: This may take 1-2 minutes to update a temperature reading for the sensor as the system is just starting up.
Fig. 2: House screen with working sensor
NOTICE: If after a few minutes of wait your screen looks like fig. 3 rather than fig. 1 then try swapping your sensor for another one and make sure all it is wired as per the Wiring Diagrams
Fig. 3: House screen with non communicating sensor
So far we have proved the Wiring Centre is working as expected and communicating with 1 sensor. You now need to rewire your sensor bus in place of the test sensor
TOP TIP: Don't forget to make sure only your last sensor has the link wire in it
STOP SYSTEMOmnie 'O' -> Cogs -> General Params -> System Set Up -> System Stop -> POP UP: Yes
TOP TIP: Once the system is stopped the Wiring Centre red LED will be flashing 3 short flashes